|product||ANSI Forged Steel Y strainer|
|product 2||ANSI Forged Steel Y filter|
|The main material||A105|
|Flange hole size||ANSI B16.5|
|Nominal diameter (MM)||1/2"-3"|
|Nominal pressure (MPA)||150LB-900LB|
|Filter element body||304|
|Flange sealing surface||（RF)/ （FF) /（FM) / （M)|
|Product Introduction||Product Introduction
KSRY14G Y strainer is an indispensable device in the transportation pipeline system. It is usually installed at the inlet end of the equipment to filter the particulate impurities in the medium to, protecting the normal use of valves and other equipment. kmo's strainer has the characteristics of advanced structure, small resistance, and convenient drainage. The applicable medium for this product is water and oil. The filter can be made according to user requirements, and the internal parts are made of stainless steel, which is more durable. The connection way includes flange type and thread screw type. The product has small size, fine filtering accuracy, good filtering effect, easy installation and maintenance, low cost, and short sewage discharge time.
Product Selection Principles
Entry and exit path: in principle, the inlet and outlet diameter of the strainer should be same as the inlet pipe diameter.
Nominal pressure：the pressure level of the strainer is according to the highest pressure that may appear in the filter line.
The choice of the number of holes: mainly consider the particle size of impurities to be intercepted, which depends on the process requirements of the medium process. (check the filter specifications for the particle size that the net can intercept)
Material: kmo recommends that the body material is generally same as the material of the connected process pipeline or the performance is higher than the pipeline material.
Notes for Installation
The product can be installed horizontally or vertically. When it is installed, the medium flow direction must be consistent with the direction of the arrow marked on the casing.
In order to maintain conveniently, it is recommended to install and use this product together with cut-off valves. Both upstream and downstream of this product should be installed with cut-off valves. When the product needs to be repaired, the upstream and downstream valves can be closed to cut off its connection with the system.
It is best to install a differential pressure gauge upstream and downstream of the product. If there is a difference between the upstream and downstream pressure gauge readings, which means that there are many impurities on the filter element. At this time, the flowing resistance will become larger, the filter element need to be cleaned.
In order to keep the system working normally when repaired the strainer, kmo recommends that it is best to install a bypass line with the strainer. The shut-off valve is closing when the strainer is working well. But when it needs to maintenance, the shut-off valve should be opened.
Please keep a space for daily maintenance and repair when installed this product.
Note for Maintenance
kmo recommends that the internal filter should be removed to clean after using a long time, so as to prevent the filter from being blocked by impurities and affecting the normal use of the system. It is generally better to clean the filter every 3 months or so.
Please check whether the filter gasket is leaky or not after the filter element re-installed. It the gasket is leaky, please replace a new one.
After installing the item in the new system, the filter screen should be cleaned in time to prevent the construction waste remaining in the pipeline from installing the pipeline to block the product.